There are 4 key areas of input to OpenSolar that determines how a battery will be modelled:
- The Battery Specifications which can you view in Control > Design & Hardware > Batteries > Edit your selected battery. These specifications determines things like the maximum charge/discharge rate, the degradation profile and rate of the battery, and the efficiency of the battery. Read more on what each of the battery specification fields do here.
- The Battery Control Scheme which sets the logic on when the battery should charge/discharge, whether it should reserve capacity to offset load at a specific time (i.e. at peak electricity rate), and if the battery is allowed to charge/discharge to the grid. You can actually create your own battery control scheme by following this guide here.
- Whether the battery is DC-connected or AC-connected (i.e. DC-coupled vs AC-coupled battery) for PV oversizing purposes.
- Load-offsettable settings which determines the portion of the load/usage that the battery can offset.
Default Battery Control Scheme
|Battery Control Scheme||Description|
In most cases you would want to select this battery control scheme. This control scheme gets the battery to:
Due to the logic that applies by this battery control scheme, it will be the best control scheme to maximise self-consumption with a battery.
This battery control scheme is generally not optimal for most system designs and is very specific for a niche use case in New Zealand. The battery will do the following:
Note: Given the niche use case of this battery logic, in most scenarios it does not result in improving electricity bill savings.
|Minimize TOU Cost (no grid charging)||
This battery control scheme is designed to maximise electricity bill savings of a Time-of-Use electricity bill by withholding capacity to offset the usage during peak electricity pricing.
Note: most cases using the "Solar-charged (Default)" control scheme will result in similar savings, since the battery discharge period generally coincides with the peak pricing periods. There are also some occasions when "Solar-charged (Default)" may have a higher bill saving than this battery logic due to the fact that the battery must withhold capacity for peak TOU periods and hence the battery may not be fully utilized to increase self-consumption.
You can create your own battery control scheme if these default schemes do not fit how your installed battery operates. Please see the guide on how to do this here.
DC-connected vs AC-connected Battery
On the Design page in the Batteries section, if you add a battery to the system design you may notice that you can set the battery to be either DC-connected or AC-connected (i.e. DC-coupled or AC-coupled battery).
OpenSolar can model the benefits of using a DC-connected battery for PV system oversizing.
What this means you can size your PV system more than the general rule-of-thumb of panel capacity being no more than 33% over the size of the solar inverter. This is because how DC-coupled batteries are connected to the system allowing excess generation output to be fed into the battery if the inverter cannot take the full output. For example, if you have a 5kW inverter and you are producing 8kW of power, 5kW of solar power can go to the inverter and the remaining 3kW can go to the battery. Oversizing does not work well with an AC-coupled battery because the 5kW solar inverter is limited to 5kW output, and the battery charging happens after the solar inverter.
Load Offsettable Settings
On the Design page in the Batteries section, you may notice there is 2 additional fields you can set. These are Load Offsettable (%) and Load Offsettable Cap (kW). These fields are used to set the portion of the load/usage that the battery can offset. One example of a use for this field is if the household is on 3-phase and the battery is only installed on one of the phase. The load offsettable fields allow you to set the portion of usage that is attributed to the phase that the battery is installed on, and hence the usage that the battery can offset.
|Load Offsettable (%)||
The percentage of the total usage that the battery can offset. Note that this will take the percentage of the usage profile that is offsettable by the battery at any given point in time.
For example if load offsettable is set at 33.33% and there is 3kWh of usage between 1-2pm, then only 1kWh between 1-2pm can be offset. However, if at 4-5pm the total usage is 6kWh, then only 2 kWh can be offset as that is 33.33% of 6kWh.
|Load Offsettable Cap (kW)||
The maximum kW of usage that can be offset by the battery.
For example if the offsettable cap is set at 5kW and the usage at 1-2pm was 8kWh, then only 5kWh can be offset by the battery.